FAQ
Home » Blog » FAQ » How generator designers determine the power factor?

# How generator designers determine the power factor?

The generator designers will have to determine the winding cross section area and specific current/mm2 to satisfy the required current, and they will have to determine the required total flux and flux variation per unit of time per winding to satisfy the voltage requirement. Then they will have to determine how the primary flux source will be generated (excitation), and how any required mechanical power can be transmitted into the electro-mechanical system, with the appropriate speed for the required frequency.
In all the above, we can have parallel paths of current, as well as of flux, in all sorts of combinations.

1) All ordinary AC power depends on electrical induction, which basically is flux variations through coils of wire. (In the stator windings).
2) Generator rotor current (also called excitation) is not directly related to Power Factor, but to the no-load voltage generated.
3) The reason for operating near unity Power Factor is rather that it gives the most power per ton of materials used in the generating system, and at the same time minimises the transmission losses.
4) Most Generating companies do charge larger users for MVAr, and for the private user, it is included in the tariff, based on some assumed average PF less than unity.
5) In some situations, synchronous generators has been used simply as VAr compensators, with zero power factor. They are much simpler to control than static VAr compensators, can be varied continuously, and do not generate harmonics. Unfortunately they have higher maintenance cost.
6) When the torque from the prime mover exceeds a certain limit, it can cause pole slip. The limit when that happens depends on the available flux (from excitation current), and stator current (from/to the connected load).

Calculate (3 + 5) =

You may also like:

1. To reduce the manpower & the CTC due to them. 2. Few skilled technicians can run the automated machines smoothly, with much lesser number of errors & faults (as human is not directly controlling ...
Grounding impedance of the transformer and building ground rods is mainly for voltage stabilization and under normal conditions should have nothing to do with our return ground fault current. See NEC 250.1 (5) ...
If you are using soft starters now, do not take them out. These are really large motors and starting them across the line is not a good idea. The utility serving you should have designed their service based on ...
Modulating Supply & Return Fans are used as a means of providing proper variable air volume (VAV) control as well as building pressurization. Many such VAV systems are still largely pneumatic with static ...
NGR stands for Neutral Grounding Resistor. When an earth fault current occurs on a plant, assuming that there is no external device presented to limit the earth fault current, the magnitude of the earth fault ...
Gozuk Blog: all about electric motor control & drives industries development in energy saving applications.

Featured

Like pumps, fans consume significant electrical energy while serving several applications. In many plants, the VFDs (variable ... A frequency inverter controls AC motor speed. The frequency inverter converts the fixed supply frequency (60 Hz) to a ... Motor starter (also known as soft starter, motor soft starter) is a electronic device integrates soft start, soft stop, ... Soft starter allows the output voltage decreases gradually to achieve soft stop, in order to protect the equipment. Such as the ... Soft Starter reduces electric motor starting current to 2-4 times during motor start up, reduces the impact to power grid during ...

In Discussion