# Neutral current is less than phase current?

In a balanced 3-phase system with pure sine waves, the neutral current is zero, ideally.

If there is phase imbalance, it shows up in the neutral, so check for imbalance.

The other major cause of high neutral currents is full wave rectification, where the current of each phase is flowing only at its peak voltage. In this case, the neutral current can be as high as three times the phase currents, theoretically.

If you can see the frequency of the neutral current, line frequency currents indicate imbalance. Current due to full wave rectification is high in third harmonics, so it may show mostly 3 x line frequency, or be a ratty square wave at 3 x line frequency.

High neutral currents, and some resulting fires, are largely responsible for the adoption of power factor correction requirements. If your loads are balanced and pfc corrected, you should not have neutral currents.

The neutral current (In) is summation of the phase currents. And obviously, the three phases are decoupled now; and not loading Y makes Iy=0.

So In = Ir + Ib (vectorial sum). Now depending on the amount of loading, nature of loads and their respective power factors, a variety of possibilities (for neutral current magnitude and phase) arise; which may include the case of In being higher.

The statement "neutral current is usually less than phase currents" is naive and not universal.

Nonlinear loads (i.e. rectifiers as Ed mentioned above) draw significant harmonic current. In many cases the current Total Harmonic Distortion (THD) is >100%. In a 3-phase, 4-wire system, the triplen harmonic currents (3, 9, 15, 21...) sum in the neutral wire because they are all in-phase. This is why the neutral current can be much higher than the phase currents even on an otherwise balanced load application. If you can put a current probe on the neutral and look at the waveform - you can see how much fundamental vs. harmonic current there is.

If there is phase imbalance, it shows up in the neutral, so check for imbalance.

The other major cause of high neutral currents is full wave rectification, where the current of each phase is flowing only at its peak voltage. In this case, the neutral current can be as high as three times the phase currents, theoretically.

If you can see the frequency of the neutral current, line frequency currents indicate imbalance. Current due to full wave rectification is high in third harmonics, so it may show mostly 3 x line frequency, or be a ratty square wave at 3 x line frequency.

High neutral currents, and some resulting fires, are largely responsible for the adoption of power factor correction requirements. If your loads are balanced and pfc corrected, you should not have neutral currents.

The neutral current (In) is summation of the phase currents. And obviously, the three phases are decoupled now; and not loading Y makes Iy=0.

So In = Ir + Ib (vectorial sum). Now depending on the amount of loading, nature of loads and their respective power factors, a variety of possibilities (for neutral current magnitude and phase) arise; which may include the case of In being higher.

The statement "neutral current is usually less than phase currents" is naive and not universal.

Nonlinear loads (i.e. rectifiers as Ed mentioned above) draw significant harmonic current. In many cases the current Total Harmonic Distortion (THD) is >100%. In a 3-phase, 4-wire system, the triplen harmonic currents (3, 9, 15, 21...) sum in the neutral wire because they are all in-phase. This is why the neutral current can be much higher than the phase currents even on an otherwise balanced load application. If you can put a current probe on the neutral and look at the waveform - you can see how much fundamental vs. harmonic current there is.

We get at the poles of the system by looking at the characteristic equation, 1+T(s). Unfortunately, we don't have the math available (except in classroom exercises) we have an empirical system that may or may ...

The potential for variable frequency drive (VFD) energy saving from slowing down the load depend on the characteristics of the load being driven. There are three main types of load: variable torque, constant ...

A completely sensor-less control would be completely open-loop, which isn't reliable with some motors like PMSMs. Even if you knew the switching instants for one ideal case, too many "random" variables could ...

As per Torque/Slip characteristic for AC Motor, the value of the Max. Torque can be developed is constant while the Starting Torque occurs @ S=.1, (T proportional to r2 and S also proportional to r2 where r2 ...

1). Through this policy, it is a Systemic transfer of Public Property to Private Companies, despite failure of many Biomass power projects and Wind mills with a great loss of Tax collection
2). Lot of Debt ...

Gozuk Blog: all about electric motor control & drives industries development in energy saving applications.

Like pumps, fans consume significant electrical energy while serving several applications. In many plants, the VFDs (variable ...
A frequency inverter controls AC motor speed. The frequency inverter converts the fixed supply frequency (60 Hz) to a ...
Motor starter (also known as soft starter, motor soft starter) is a electronic device integrates soft start, soft stop, ...
Soft starter allows the output voltage decreases gradually to achieve soft stop, in order to protect the equipment. Such as the ...
Soft Starter reduces electric motor starting current to 2-4 times during motor start up, reduces the impact to power grid during ...

ONE of my diesel generator 1400kva trips down

Problems overcoming check valve on fire pump system

question: I am in a debate concerning motion.

How much investment in solar power plant for 100kw?

Spur growth and demand for Electric Motors in India.

Should SCADA PC, HMI, PLC, DCS be on the same existing IT NETWORK

Induction motor 415 volt, 16A FLA taking current 9A, 29A, 21A

Are there any zero installation, Windows based, stand-alone HMIs?

Problems overcoming check valve on fire pump system

question: I am in a debate concerning motion.

How much investment in solar power plant for 100kw?

Spur growth and demand for Electric Motors in India.

Should SCADA PC, HMI, PLC, DCS be on the same existing IT NETWORK

Induction motor 415 volt, 16A FLA taking current 9A, 29A, 21A

Are there any zero installation, Windows based, stand-alone HMIs?