Wiki
Home » Blog » Wiki » Harmonic current

# Harmonic current

I hate to call them harmonic currents. The do submit to Fourier analysis, but you are probably dealing with AC to DC power supplies. If you look at the current pulses, you will see that each pulse is about 1-2 milliseconds in duration in alternating directions. If you sum these all in the neutral there is the appearance of what looks like 180 Hertz in the neutral. If you use different sized power supplies on each phase, you can see that it is just the addition of the three phases. So the neutral current when you have non power factor corrected power supplies is the sum of the three phases. Unless the current waveforms overlap, there is no cancellation of current in the neutral, hence the neutral current is the sum of the phase currents. The reasoning behind this is the rectifier diodes in the front of the power supply and the DC storage capacitors size relative to the DC load on the capacitor. The general rule of thumb is that the capacitor is about 800 to 1000 microfarads per amp of current in the capacitor.

Realize that the extra heating in the three phase delta-wye transformers is due to the extra circulating current in the primary delta causing excessive heating of the primary conductor. The world calls transformers designed to deal with this "K" factor transformers. Let the world of electrical engineers bury all this simple stuff behind the maze of Fourier analysis. Change the incoming voltage slightly and your Fourier analysis is garbage. The issue here is switches and storage caps--- not some magical mathematical garbage.

By the way if someone wanted to use the wire sizing guidelines of the National Electrical Code in the US to size wire for 100% power supply load, the neutral wire would be 8 gauge sizes larger than the phase conductors. People need to start demanding PFC power supplies. Fix a switching problem with switches.

Calculate (9 + 8) =

You may also like:

Variable frequency drive power anomalies can be divided into following three types: phase loss, low voltage and power off, sometimes they maybe appear mixed. The main reasons for these anomalies are ...
For a "physical" interpretation, reactive current (power/KVA flow), in my opinion is best looked at from the perspective of a generator connected directly to an infinite bus (in LV generators this is the norm).
Coming from a signal processing and communications theory background, but with some experience in power design, I can't resist the urge to chime in with a few remarks. There are many engineering methods to ...
Can an AC drive to replace the mechanical gearbox that used to decrease motor speed in conveyor application i.e to use a motor that will drive the load directly throw a coupling, belt or chain, without ...
The high frequency edges of switched waveforms can cause capacitively coupled currents to flow from windings to frame, returning through the bearings, and these can accelerate corrosion in the bearings, ...
Gozuk Blog: all about electric motor control & drives industries development in energy saving applications.

Featured

Like pumps, fans consume significant electrical energy while serving several applications. In many plants, the VFDs (variable ... A frequency inverter controls AC motor speed. The frequency inverter converts the fixed supply frequency (60 Hz) to a ... Motor starter (also known as soft starter, motor soft starter) is a electronic device integrates soft start, soft stop, ... Soft starter allows the output voltage decreases gradually to achieve soft stop, in order to protect the equipment. Such as the ... Soft Starter reduces electric motor starting current to 2-4 times during motor start up, reduces the impact to power grid during ...

In Discussion