Wiki
Home » Blog » Wiki » Calculate current setting of overcurrent relay

Calculate current setting of overcurrent relay

You can calculate current setting of overcurrent relay by using next expression:

Isetting ≥ (ks*Imaxopam)/(a*pi)
Imaxopam=kam*Imaxoptr

where are:

Isetting-current setting of overcurrent relay
ks-safety coefficient
Imaxopam-maximum operational current under which overcurrent relay shouldn't to act
a-coefficient of layoffs overcurrent relay (0,85-0,95)
pi-ratio of current transformer
kam-coefficient which describes influence of common starting of all asynchronous electrical motors in the appropriate power network after elimination of fault (1-6)
Imaxoptr-maximum operational current of power transformer

Besides I have already explained meanings of all appropriate sizes, I would like to underline differentiate between Imaxopam and Imaxoptr.
Imaxoptr is maximum operational current of power transformer in normal conditions while Imaxopam is maximum operational current of power transformer after interruption of fault and mentioned current includes influence of common starting of all asynchronous electrical motors in the appropriate power network after elimination of fault. It is very important to say that appearing of fault in power network leads to significant decreasing of voltage what has a consequence deceleration of all asynchronous electrical motors in appropriate power network. After interruption of fault, it comes to appearing of process during which all asynchronous electrical motors are starting in some parts of power network which are still turned on. This is situation which is significant different from situation where asynchronous electrical motors are starting one by one while in this case all asynchronous electrical motors are starting at the same time. Because of this fact, after elimination of fault, value of current isn't same as value of current before appearing of fault. After elimination of fault, value of current, which I called Imaxopam, is higher than value of operational current of power transformer, which I called Imaxoptr, but under those conditions there is no fault, so current setting of overcurrent relay should to be set on that value of current and mentioned relay shouldn't act under those conditions.

After calculation of current setting of overcurrent relay, you need to check coefficient of sensitivity of acting of overcurrent relay by using next expression:

ksens=Ifmin/(Isetting*pi)

where are:

ksens-coefficient of sensitivity of acting of overcurrent relay
Ifmin-minimum fault current (1 phase fault to the earth or 2 phases fault)
Isetting-current setting of overcurrent relay
pi-ratio of current transformer

Value of coefficient of sensitivity of acting of overcurrent relay should to be higher or equal with 1,5 in case when is fault at opposite busbars (busbars where isn't overcurrent relay) or higher or equal with 1,2 in case when is fault at the end of the longest feeder which begins at those opposite busbars. Time setting should to be selected like that overcurrent relay needs to wait acting of another protection which is on the feeders (for example distance protection).

Calculate (9 + 7) =

You may also like:

1. How does this affect the vector group (YNd1) of the transformer? Will it be changed to YNd11? 2. Will it make any difference as far as the vector group is concerned if instead of phase A and C, phase B ...
A 1:1 ratio transformer is primarily used to isolate the primary from the secondary. In small scale electronics it isolates the noise / interference collected from the primary from being transmitted to the ...
Where we really need digital communication networking, in my personal opinion, is down at the sensor/transmitter and positioner/actuator/valve level to take the place of 4-20 mA and on/off signals. Down at the ...
I work across the scale of power electronics in voltages and currents. From switchers of 1W for powering ICs to 3kW telco power supplies up to multi-megawatt power converters for reactive power control in AC ...
At zero speed the motor requires torque which is flux (voltage) and current (mostly reactive). Only a little bit of active current to compensate for the motor power losses. Only the power losses need to be ...
Gozuk Blog: all about electric motor control & drives industries development in energy saving applications.

Featured

Like pumps, fans consume significant electrical energy while serving several applications. In many plants, the VFDs (variable ... A frequency inverter controls AC motor speed. The frequency inverter converts the fixed supply frequency (60 Hz) to a ... Motor starter (also known as soft starter, motor soft starter) is a electronic device integrates soft start, soft stop, ... Soft starter allows the output voltage decreases gradually to achieve soft stop, in order to protect the equipment. Such as the ... Soft Starter reduces electric motor starting current to 2-4 times during motor start up, reduces the impact to power grid during ...

In Discussion