Wiki
Home » Blog » Wiki » Full load torque VS Rated torque

# Full load torque VS Rated torque

All motors have a "torque vs speed" characteristic.

DC machines are very simple: constant torque from zero speed to some "base speed", and then a "constant power" ranging from base speed to top speed. In the constant torque range, acceleration is dependent on applied voltage, with the field under constant full current excitation. In the constant power range, voltage is held constant and the field current is reduced, thereby achieving an increase in speed (hence the term "field weakening").

AC machines are somewhat more complex, since the curves are nowhere near as linear. The key points are:
- "starting torque", which is the torque achieved at the locked rotor (zero speed) condition
- "pull in torque", which is the available machine torque at the point where the machine pulls into synchronism (synchronous machines only)
- "pull out or breakdown torque", which is the peak torque the machine can sustain momentarily before stalling
- "load torque", which is the amount of torque actually required by the process at any operating point
- "accelerating torque", which is the difference between what the machine is capable of producing and the load torque

A machine is rated for the "full load torque" condition which is the rated torque performance of the machine. In imperial (lb.ft) units, that would be 5252 * HP / RPM. It can produce this torque continuously, provided it has the rated conditions of applied terminal voltage and applied terminal current (for both rotor and stator, as applicable).

The time required to start a motor is dependent primarily on the accelerating torque available and the combined inertia (motor + remainder of drive train).

Note that available starting and pull-in torque during the transient operation of starting is proportional to the square of the applied voltage - if the voltage dips below 1.0 per unit, the available torque will be significantly reduced.

When operating an AC machine on a variable frequency drive, the most common approach is to mimic the DC curves. This is done by using a constant volt/hertz ratio until a "base" speed is achieved at rated terminal volts. Typically, this occurs at line frequency. For "extended" or "field weakening" operation, the terminal voltage is held constant and the applied frequency allowed to increase to obtain the desired speed.

Calculate (8 - 1) =

You may also like:

The aforementioned types of Circuit Breakers are used in LV System and generally based on the same operating principle. MCB and MCCB/ICCB have a bimetal heater for overload which releases the Contact s while ...
In inverter regular inspection, we must cut off power before operation. Wait 4minutes (the bigger the longer, the maximum waiting time is 15 minutes) till the frequency inverter display panel LED indicator ...
For flyback & boost applications, powder cores such as Kool-mu, Xmu, etc... are usually best performing and lowest cost. Even these may need to be gapped and if CCM operation is required, a "stepped-gap" ...
There are two important different parameters as far as the disconnection/connection of Electrical utilities is concerned. - Breaking capacity. - Making Capacity.
The method of creating a die-cast rotor is as follows: 1. An assembly of steel laminations (which may or may not be grain-oriented) containing the openings for both rotor bars and ventilation (as required) is ...
Gozuk Blog: all about electric motor control & drives industries development in energy saving applications.

Featured

Like pumps, fans consume significant electrical energy while serving several applications. In many plants, the VFDs (variable ... A frequency inverter controls AC motor speed. The frequency inverter converts the fixed supply frequency (60 Hz) to a ... Motor starter (also known as soft starter, motor soft starter) is a electronic device integrates soft start, soft stop, ... Soft starter allows the output voltage decreases gradually to achieve soft stop, in order to protect the equipment. Such as the ... Soft Starter reduces electric motor starting current to 2-4 times during motor start up, reduces the impact to power grid during ...

In Discussion